Requirements for inspections are dependent on the type of construction taking place. Please select from the options below in order to find out what requirements the inspector will be looking for:
Special Note: All approved building permit drawings, manufacturers shop drawings and details, necessary certifications and prior approval of location survey submission must be in place prior to requesting this roof framing inspection.
Special Note: All approved building permit drawings, manufacturers shop drawings and details, necessary certifications and prior approval of location survey submission must be in place prior to requesting this wall framing inspection.
Special Note: Advise the job Supervisor that flashings and weep holes are required in all masonry walls, at foundations, over doors and windows, and as a protection for attached wood trim and decks.
Services, Feeders and System Grounding Inspections
General Inspections for All Areas
Kitchen Area Inspections
Dining Room Area Inspections
Bathroom Area Inspections
Other Habitable Area Inspections
(Bedrooms, Family Rooms, Dens, etc.)
Hallway Area Inspections
Laundry Area Inspections
Basement and Attic Inspections
(Attached or with Electric Power)
Service Equipment Inspections
Verify that a suitable wiring method of Chapter 3 of the NEC is used to supply and connect spas and hot tubs, unless cord and plug connections are permitted.
Verify that at least one GFCI-protected receptacle on a general-purpose branch circuit is located between 5 ft and 20 ft. (1.42 m and 3.05 m) of the walls of the spa or hot tub.
Verify that any receptacles used to supply power to a spa or hot tub are GFCI protected.
Verify that lighting fixtures are spaced as required from spa or hot tub walls and above maximum water level, and that GFCI protection is provided, as required.
Verify that wall switches are located at least 5 ft. (1.52 m) from the inside walls of the spa or hot tub.
Verify that all parts required to be grounded or bonded are grounded or bonded using appropriate methods.
Check electric pool heaters for listing, subdivision of heating elements, and sizing of branch-circuit conductors.
CCheck underwater audio equipment for compliance with Parts B or C of Article 680.
Review definitions and determine applicability of Part F of Article 680.
Check therapeutic pools and tubs for suitability for approval.
Verify that permanently installed therapeutic pools comply with the applicable requirements for permanently installed pools, Parts A and B of Article 680.
Verify that outlets for therapeutic tubs are GFCI protected (separate or integral) unless supplying field assembled tubs rated 3-phase or over 250 volts.
Verify that all therapeutic equipment is GFCI protected.
Verify that all parts of therapeutic tubs required to be grounded or bonded are grounded or bonded using appropriate methods.
Verify that all receptacles within 5 ft. (1.52 m) of a therapeutic tub are GFCI protected.
Verify that all lighting fixtures used in areas of therapeutic tubs are of the totally enclosed type.
Review definitions and determine applicability of Part G of Article 680.
Check hydro massage bathtub equipment for suitability for approval.
Check hydro massage bathtub equipment for GFCI protection.
Check other electrical equipment in the same room as a hydro massage bathtub for compliance with the ordinary rules of NEC Chapters 1 through 4.
Verify that hydro massage bathtub equipment is accessible without damaging the building structure or finish.
Verify that metal parts required to be bonded are connected together with a minimum No. 8 solid copper bonding jumper.